Boiler 3 Inspection
St-Joseph Mercy – Ann Arbor Campus
A visual Inspection was performed on Boiler 3. Below please find attached pictures and observation.
Attention: Alex Lobodocky, SJMHS
Paul Dobry, SJMHS
Sonny Greeno, Chubb
Eldon Water Representative: Joseph Ham, B.Sc.E
Patrick Racine, P.Eng. CEM
Mech. Con. Co.: DJ Conley Mech. Con. Rep.: Eric Cameron
Type: Water Tube Op Pressure PSI: 80 psig
System Information: Hosp.HVAC Water Treatment: Eldon Water Inc.
Application: Heating, humidity Pretreatment: Duplex Softener, Duplex Dealkalizer
% Returns: 95% Products Used: Oxikor S1100, Quest 250S, Caus 50
Op Hours: 24/7 App. Method: Meter initiated feed
Inspection Point: Steam Drum
Deposits: no signs of scale deposit.
Corrosion: small signs of oxygen pitting on left baffle plate. Same as last year
Inspection Point: Mud Drum
Deposits: no signs of scale deposits on tube. Small build up at end of tubes.
Corrosion: no signs of oxygen pitting
· Ensure daily water tests are within recommended ranges for operating boiler, especially sodium sulfite, polymer and hardness levels.
· Ensure proper warm lay-up procedures are followed. These were emailed to you last month. Please contact us for more details on this.
· Weekly water tests should be performed on lay-up boiler.
· Continue on-going chemical treatment.
Thank you for your continued interest in our services and products,
Patrick Racine, P.Eng., CEM
Eldon Water Inc. – The Water Specialists
888.712.4000 ext 802