Warmed #3 boiler, blewdown and checked L.W.C.O. on #1 boiler
Test and log boiler and tower water results.
Met Joe Hamm, he found problem with yard tower webmaster and made repair.He could not find problem with webmaster for #3and #4 tower’s.
I put boiler chemical pumps back on relay control from water meter.
Adjusted pumps up.
Talked to ARCH envoriomental rep. George,he said the Veeder Root alarm ( sudden loss ) will be OK until he comes in on the 17th.