Plant rounds and readings in the Energy Center. Warmed #3 Boiler, Blew down #1 Boiler and checked LWCO. Tested boiler water and cooling towers water. Med gas Manifold readings. Metasys Checks and Cold and/or warm calls.
Added 2gal. of halochlor to yard tower.
Changed boiler chemical Oxykor S1100 from 40 to 45.
Worked on P.M.’s with Tom.