Plant rounds and readings in the Energy Center. Warmed #3 Boiler. Blew down #1 Boiler and checked LWCO. Tested boiler & Cooling tower water and logged. Med gas Manifold readings. Metasys Checks and Cold and/or warm calls.
Shutdown Chiller #1 , closed condenser valve and took override off yard tower pump#2.
Reset RHC dom. pump #12
Several Room Pressure alarms from OSC Hybrid OR room #1
Chiller #1 came back on line opened condenser valve and put override on pump #2