Plant rounds and readings in the Energy Center. Warmed #1 Boiler. Blew down #3 Boiler and checked LWCO. Tested boiler & Cooling tower water and logged. Med gas Manifold readings. Metasys Checks and Cold and/or warm calls.
Surge Tank – pulled control float Ok, Flushed lines and checking system it is working like it should, must of had something in seat of control valve.
Had to reset alarms and restart fans after fire system testing.