Fungi / Yeast
Roof Tower 3
Roof Tower 4
Plant rounds and readings in the Energy Center. Warmed #1 Boiler. Blew down #3 Boiler and checked LWCO. Tested boiler & Cooling tower water and logged. Med gas Manifold readings. Metasys Checks and Cold and/or warm calls. Added salt. worked on P.M.’s
started opening humidifiers- 7,9,17.
Winter air taps for CW coils have been installed. Most tubing and fittings have been installed. Will try to finish up Thurs. The CW coils do not have access taps. The pressure gagues will have to be removed and the hose fittings installed in there place. The fittings have been left at each coil.
MER AHUS have been set up for winter CW coil drying. Some fittings will have to be removed and a 90 will have to be installed for clearence. Fittings have been left in place for installation.