Warmed and blew down boilers test and log boiler water results. Hosed out basin on #4 cooling tower opened ball valves on balancing tanks Have not removed screens yet,normal shift
Routine Shift Duties
Rounds and readings-metasys-hot/cold calls-normal shift
Turn off make-up valve-open CT drain lines-turn off chiller at chiller panel.
Close make-up water vale-open CT drain lines-turn off cond pumps-turn off CT fans freq drive-turn off CW pumps freq drives. Will check 11-12-14.
Replaced pressure switch on small bakery oven
Warmed and blew down boilers checked L.W.C.O. on #3 boiler Test and log bolier water results,finished cleaning #3 cooling tower, added ecoklenz to #4 cooling tower,asking Bill Metzger to drain make up and basin at shut down tonight.
Replaced two fan belts serving the GROSSING STATION & general exhaust needs of AP. Ordered six replacement belts (A38) from GRAINGER, req. # 8106323