Close make-up water vale-open CT drain lines-turn off cond pumps-turn off
CT fans freq drive-turn off CW pumps freq drives. Will check 11-12-14.
Replaced pressure switch on small bakery oven
Warmed and blew down boilers checked L.W.C.O. on #3 boiler
Test and log bolier water results,finished cleaning #3 cooling tower,
added ecoklenz to #4 cooling tower,asking Bill Metzger to drain make up and basin
at shut down tonight.
Replaced two fan belts serving the GROSSING STATION & general exhaust needs of AP. Ordered six replacement belts (A38) from GRAINGER, req. # 8106323
Work was completed today by Keith from J.E.G. to complete restoration of steam serving M.E.R. 9 Any isolation valves closed off for the summer months will still need attention. Next to receive similar treatment is M.E.R. 5 just waiting for a replacement relief valve ordered from VR.