Close make-up water vale-open CT drain lines-turn off cond pumps-turn off CT fans freq drive-turn off CW pumps freq drives. Will check 11-12-14.
Replaced pressure switch on small bakery oven
Warmed and blew down boilers checked L.W.C.O. on #3 boiler Test and log bolier water results,finished cleaning #3 cooling tower, added ecoklenz to #4 cooling tower,asking Bill Metzger to drain make up and basin at shut down tonight.
Replaced two fan belts serving the GROSSING STATION & general exhaust needs of AP. Ordered six replacement belts (A38) from GRAINGER, req. # 8106323
Work was completed today by Keith from J.E.G. to complete restoration of steam serving M.E.R. 9 Any isolation valves closed off for the summer months will still need attention. Next to receive similar treatment is M.E.R. 5 just waiting for a replacement relief valve ordered from VR.
Routine Shift Duties
I found the motor mount had a crack in it, it cause the belt to fall off. No parts in stock, will replace tomorrow. Unit is off, (E-1015)
Warmed and blew down boilers checked L.W.C.O on #3 boiler Test and log boiler water results,started dip slide for #4 tower Cleaning #3 roof tower,normal shift