The water supply feeding the radiant system for our 5305 Building has been valved off at the fill valve. A copper coupling is leaking in the Dr. McMurtrie’s office ( southeast corner of the 2nd floor). Brandon & Jim investigating options for repair. As a ‘just in case’ I have commanded Radiant Pumps 1 & 2 off in METASYS.
Lowered D.A.T. set points from 65 to 55 on all three rooftop units serving the 5305 building. Complaint of high humidity causing paper issues in Administration. Brad will measure % RH this morning and follow up tomorrow or Fri to confirm the lower d.a.t. was effective.