Slightly opened up shut off valve to MER 5 low pressure Leslie. Shut off valve and Leslie leaks by, but ahu 7-5 is hogging all the steam due to the cooler weather. *Heat for Meditation garden/mer 29 is also fed off this system.
Relief valve open on 2nd stage steam reducing station in mer 5. Check setting, prv is bleeding by when no load is on it. Valved off, valve not holding all the way, but shouldn’t lift relief valve. !st stage is also high, will look more into this next week- might by on the steam shut down list.
Humidifiers valved off in Meditation Garden and MER 5