Found ahu 50-30 running at 46 degrees, cooling valve 18% open. Shut down fan, power cycled jci panel. Restart, currently holding setpoint
5th floor static pressure in alarm on ahu 43-26. Noticed static pressure set point on ahu was set at .5, don’t know why this was changed. Put back to 1.0″ alarm went back to normal.