John E Green pulled both pumps and removed large amounts of towels around the impellers. They reinstalled the pumps and the electricians verified amp draw of around 4 amps. Pumps have been put back into normal operation.
Found sewage pumps tripped on overloads. Reset and pumped water down. Pumps tripped again. Had Electricians check out. Currently trying to find pump info for amperage. Also pipe has hole inside the pit. Referred to John E Green for repairs.