Utility readings-metasys-cold calls-healthstream-temptrack-rounds and readings-normal shift
A.F. Smith removed & replaced failed return air VFD. Commissioning will be completed next week by SSI, until then, do not use (has been off all summer!)
- Tim Napier from Health Choice Services will be completing a semi-annual waste anesthetic gas analysis beginning today after 3- through Thursday night. Work will be completed at CANTON, Brighton, Livingston, ASF, M.O.S.C., Surgery Pavilion, and CCH. Work will be completed in any area where anesthetic gases are used, i.e. surgery, angio, cath lab, etc. Security & management for these areas have been pre-notified. If there’s need to contact Tim do so at: 502.541.1711.
warmed and blew down boilers checked L.W.C.O. on #3 boiler
test and log boiler water results. tighten manhole covers on #2 boiler.
Plant rounds and readings in the Energy Center.
Warmed #1 Boiler, Blew down #3 Boiler and checked LWCO on both.
Tested boiler water 3 times and cooling towers water.
Med gas Manifold readings.
Metasys Checks and Cold and/or warm calls.
Added 2.5 gal. of Halochlor and 1qt. of Defoamer to Yard Tower.
Added 1qt. of Halochlor to #3 Tower.
On #2 Boiler warmed header and opened header valve. Started boiler and checked Low water alarm, Low Water cut out, and Auxiliary Low Water cut out. Warmed up and Put boiler on line. Put Boiler in manual, local with burner off.
Helped Bill McCarthy change Filters.