Rumor has it ,we will not be circulating chilled water this fall, before we drain for the season. Not a good idea. I have witness frozen coils on the old Trane units. These units have poor air mixing, air stratification, questionable freeze stats and steam coils that are in poor shape. Count me out for repairing chilled water coils and flood control, I am on the record.
changed filters in MER 5,10, and A/C 38 and 39-20. Sorted final filters in plant
Utility readings-metasys-cold calls-healthstream-temptrack-rounds and readings-normal shift
A.F. Smith removed & replaced failed return air VFD. Commissioning will be completed next week by SSI, until then, do not use (has been off all summer!)
Tim Napier from Health Choice Services will be completing a semi-annual waste anesthetic gas analysis beginning today after 3- through Thursday night. Work will be completed at CANTON, Brighton, Livingston, ASF, M.O.S.C., Surgery Pavilion, and CCH. Work will be completed in any area where anesthetic gases are used, i.e. surgery, angio, cath lab, etc. Security & management for these areas have been pre-notified. If there’s need to contact Tim do so at: 502.541.1711.