warmed and blew down boilers checked L.W.C.O. on #3 boiler
test and log boiler water results. tighten manhole covers on #2 boiler.
Plant rounds and readings in the Energy Center.
Warmed #1 Boiler, Blew down #3 Boiler and checked LWCO on both.
Tested boiler water 3 times and cooling towers water.
Med gas Manifold readings.
Metasys Checks and Cold and/or warm calls.
Added 2.5 gal. of Halochlor and 1qt. of Defoamer to Yard Tower.
Added 1qt. of Halochlor to #3 Tower.
On #2 Boiler warmed header and opened header valve. Started boiler and checked Low water alarm, Low Water cut out, and Auxiliary Low Water cut out. Warmed up and Put boiler on line. Put Boiler in manual, local with burner off.
Helped Bill McCarthy change Filters.
Changed filters in MERs 6,7,9,18 and 19 and removed old filters
Warmed and blew down boilers ,checked L.W.C.O on #1 boiler.
test and log water results.
pumped in sulfite in to #1 boiler to bring up to stand by levels 450
Rotate boilers,put #3 as lead.
Put manhole covers back on #2 boiler and started filling added chemicals before filling
Per Amy Conners/Pierre Gonyon raised r.a. humidity set point from 35% to 40% ~ on going I.A.Q. complaints; ‘watery eyes’. I intentionally put this in as an operator override to draw attention to it. If there’s need to alter, please lemme know or Pierre… Thanks! b.