Found meditation garden at 62 degrees. Metasys wouldn’t open steam valve. Shut down fan, power cycled dx. Restarted fan, started controlling properly
Blowdown boiler 1.
Warm up boiler 3.
Monitor metasys – adjust/dispatch as needed.
Plant rounds and readings.
Work on tower walchems – Tower 3/4 and yard now back on line.
Work on metasys graphics – North tower, generators.
Work on engineering blog.
Power plant Rounds and readings
Yard Tower Walchem is back on line – http://10.64.172.248/htm_login.htm
Towers 3 and 4 Walchem is back on line – http://10.64.172.250/htm_login.htm
AHU 1-16, A2444, Replaced the diaphrams on the Actuator for the Reheat for the Cafe seating area.