Power plant Rounds and readings
Yard Tower Walchem is back on line – http://10.64.172.248/htm_login.htm
Towers 3 and 4 Walchem is back on line – http://10.64.172.250/htm_login.htm
AHU 1-16, A2444, Replaced the diaphrams on the Actuator for the Reheat for the Cafe seating area.
Check for source of leak on dishwasher on Meadows. Service for Hobart has been called and they will be out tomorrow 10/18.
Plant rounds and readings in the Energy Center. Warmed #3 Boiler, Blew down #1 Boiler and checked LWCO. Tested boiler water and cooling towers water. Med gas Manifold readings. Metasys Checks and Cold and/or warm calls.
Added 2gal. of halochlor to yard tower.
Changed boiler chemical Oxykor S1100 from 40 to 45.
Worked on P.M.’s with Tom.