Changed out pre-filters in MER 8,16,17,25 and moved filters up to MER 18 and 19
Blowdown boiler 1.
Warm up boiler 3.
Monitor metasys – adjust/dispatch as needed.
Plant rounds and readings.
Work on tower walchems.
Chiller 2 started at 8pm? Stopped.
power plant rounds and readings
received 5 skids of air filters
Routine Shift Duties.
Added 2 gals. Halochlor C to the basin of the yard tower and circulated.
Changed Boiler Caus 50 pump setting from 32 to 35.
Changed Oxykor S1100 pump setting from 47 to 50.
Changed Quest 250S pump setting from 47 to 50.
Utility readings-metasys-rounds and readings-shut off chiller 2 6p.m.-chiller 2
tried to restart at 8p.m. shut it off-do dip slides for yard and tower 3-normal shift