Check for source of leak on dishwasher on Meadows. Service for Hobart has been called and they will be out tomorrow 10/18.
Plant rounds and readings in the Energy Center. Warmed #3 Boiler, Blew down #1 Boiler and checked LWCO. Tested boiler water and cooling towers water. Med gas Manifold readings. Metasys Checks and Cold and/or warm calls. Added 2gal. of halochlor to yard tower. Changed boiler chemical Oxykor S1100 from 40 to 45. Worked on P.M.’s with Tom.
Changed out pre-filters in MER 8,16,17,25 and moved filters up to MER 18 and 19
Blowdown boiler 1. Warm up boiler 3. Monitor metasys – adjust/dispatch as needed. Plant rounds and readings. Utility readings. Eldon meeting. Work on tower walchems. Chiller 2 started at 8pm? Stopped.
power plant rounds and readings engineering meeting received 5 skids of air filters normal shift