Routine Shift Duties. Added 2 gals. Halochlor C to the basin of the yard tower and circulated. Changed Boiler Caus 50 pump setting from 32 to 35. Changed Oxykor S1100 pump setting from 47 to 50. Changed Quest 250S pump setting from 47 to 50.
Utility readings-metasys-rounds and readings-shut off chiller 2 6p.m.-chiller 2 tried to restart at 8p.m. shut it off-do dip slides for yard and tower 3-normal shift
Power plant rounds and readings Normal shift
Defrosted 3 East Breast Milk fridge
REF? E5918, replaced Belt 4L270.